for Brooklyn Center, MN
Our Reviews by City
Matt - Brooklyn Center, MN
Complicated older a/c issues
John - Brooklyn Center, MN
Got very thorough and expert opinion for dispute related to s warranty claim.
great customer service
Brad - Brooklyn Center, MN
Jeff - He went out of his way after I accidentally butt dialed him after he left! he called and stopped by the next day to make sure everything was working properly! So customer service award to Jeff!!! oh and sorry Jeff!
Robert - Brooklyn Center, MN
Service rep did a thorough job and was friendly
Scott - Brooklyn Center, MN
Great service and value
Bob - Brooklyn Center, MN
We have worked with three furnace companies in the last year, Comfort Matters is the best value by far.
John - Brooklyn Center, MN
Wes put the comfort in "Comfort Matters"! He was very professional and respectful. I'm sure the rest of your team is as great as him!
Dylan - Brooklyn Center, MN
Replace existing air conditioner with Daikin 13 SEER A/C
Customer explained water leaking from furnace when ac would run. Ran ac and found ice on refigerant lines. Removed and replaced dirty filter with clean one to ensure good airflow. Recommended we conduct a tune up to verify proper operation. Perfomed an AC precision tune up. Clean and tune up AC; cleaned condenser coil, checked all outdoor electrical components, tested indoor air flow, checked refrigerant levels, and tested overall AC operation. Found the system to be low on R22 refigerant. To get unit up and cooling properly, would have to charge with refigerant, add a leak seal to attempt at stopping refigerant leak, and install locking caps. Electrical components and outdoor unit showing age and are in need of replacement. Motor starter very burnt. Can cause poor electrical connections and lead to unit failure. Motor booster is testing out of manufacture rating and could also lead to unit failure. Customer did not want to make repairs today. Customer purchased new unit over the
Replaced Condensate Pump. Checked all PVC fittings for drain. Replaced water alarm.
Tested condensate pump multiple times and it drained correctly. I filled the Coil drain pan and it drained correctly. I ran the humidifier and noticed no leaks. I shortened the drain hose for the condensate pump so it was above the water in the water drain. I tested sub cooling and it was inside its passing parameters.I took the coil door off and checked and confirmed the drain pan was in the rails. I noticed the combustion air drain clamp was loose. Tightened it. The owner noticed the leak while cooling. I could not recreate the leak.
Furnace precision tune up; clean and tune up furnace; clean burners, test ignition components, adjust gas level, test safety circuit, check indoor motors, checked all electrical components, tested indoor air flow, checked heating temperatures, and tested overall furnace operation. Blower Wheel and Air Ducts are getting very dirty. Both are recommended to be cleaned. Will have the office follow up with you in about a week. Duct cleaning is 250$ off right now. Invoice will not show discounted price.
AC precision tune up. Clean and tune up AC; cleaned condenser coil, checked all outdoor electrical components, tested indoor air flow, checked refrigerant levels, and tested overall AC operation. Furnace precision tune up; clean and tune up furnace, clean burners, test ignition components, adjust gas level, test safety circuit, check indoor motors, checked all electrical components, tested indoor airflow, checked heating temperatures, and tested overall furnace function. Upon inspection found that the wheel that moves the air throughout the house is dirty and itâ€™s encouraged to get that cleaned to increase overall efficiency of the unit. Also found that the thermostat was causing homeowner issues and should think about replacement. Lastly due to construction of basement, changing the filter every 3 months is encouraged. All recommendations declined at this time.
Furnace tune up. Performed maintenance on Whirlpool furnace.